Larsen's Valve Cabinets
Models Available:
VC1818 and VC2626 SERIES SERIES VC4016 and VC3616 SERIES
VC1818 and VC2626 SERIES
TO SPECIFY THE VC1818 and VC2626 SERIES:
 Insert, after "VC," the appropriate prefix for the trim and door material.
If STEEL  Use S. If ALUMINUM  Use AL. If STAINLESS STEEL  Use SS.
If BRASS  Use B. If BRONZE  Use BZ.  Select the required model number from the table below.
 Select the door style from the illustrations.
The VC2626 Series is designed specifically to meet fire codes which require the continuous revolution of a 12" long spanner wrench. 
Model Number 
Trim Style and Projection 
Inside Box Dimensions H x W x D 
Outside Trim Dimensions H x W*** 
Rough Opening H x W x D 
Knockout Locations** E G 
Interior Capacity 

VC1818R  Rec. 5/16  18 x 18 x 8  21½ x 21½  19 x 19 x 8¼  9" 4"  One 2½" Fire Dept. valve with cap and chain 

FS  VC1818R  Rec. 5/16  18 x 18 x 8  21½ x 21½  20^{1/8} x 20^{1/8} x 9^{1/8}    
VC1818RK  SemiRec. 1¼  18 x 18 x 8  21½ x 21½  19 x 19 x 7¼  9" 4"  
FS  VC1818RK  SemiRec. 1¼  18 x 18 x 8  21½ x 21½  20^{1/8} x 20^{1/8} x 8^{1/8}    
VC1818RL  SemiRec. 2½  18 x 18 x 8  21½ x 21½  19 x 19 x 6  9" 4"  
FS  VC1818RL  SemiRec. 2½  18 x 18 x 8  21½ x 21½  20^{1/8} x 20^{1/8} x 7    
VC1818RT  Trimless  18 x 18 x 8    x x8½†  9" 4"  
VC1818SM  Surface Mtd.  21½ x 21½ x 8½  21½ x 21½      
VC2626R  Rec. 5/16  26 x 26 x 8  29½ x 29½  27 x 27 x 8¼  13" 4"  One 2½" Fire Dept. valve with cap and chain 

FS  VC2626R  Rec. 5/16  26 x 26 x 8  29½ x 29½  28^{1/8} x 28^{1/8} x 9^{1/8}    
VC2626RK  SemiRec. 1¼  26 x 26 x 8  29½ x 29½  27 x 27 x 7¼  13" 4"  
FS  VC2626RK  SemiRec. 1¼  26 x 26 x 8  29½ x 29½  28^{1/8} x 28^{1/8} x 8^{1/8}    
VC2626RL  SemiRec. 2½  26 x 26 x 8  29½ x 29½  27 x 27 x 6  13" 4"  
FS  VC2626RL  SemiRec. 2½  26 x 26 x 8  29½ x 29½  28^{1/8} x 28^{1/8} x 7    
VC2626RT  Trimless  26 x 26 x 8    x x8½†  13" 4"  
VC2626SM  Surface Mtd.  29½ x 29½ x 8½  29½ x 29½     
VC4016 and VC3616 SERIES
Larsen's exclusive VC4016 and VC3616 Series provide an attractive, innovative, and economical method of housing a fire extinguisher and a fire department valve. Both the VC4016 and VC3616 support the extinguisher with a heavy gauge shelf. The shelf in both units is located 12" up from the bottom of the cabinet, leaving approximately 28" for the extinguisher height in the VC4016 and 24" in the VC3616.
A more economical option is available for both units. As pictured at the left, the shelf can be deleted with the valve installed at the top of the cabinet. With this option, the "F" dimension for the knockout location (see chart at left) is measured from the top of the cabinet. To specify this unit, see below.
TO SPECIFY THE VC4016 and VC3616 SERIES:
 Insert, after "VC," the appropriate prefix for the trim and door material (please refer to page 13).
If STEEL  Use S. If ALUMINUM  Use AL. If STAINLESS STEEL  Use SS.
If BRASS  Use B. If BRONZE  Use BZ.
 Select the required model number from the table below.
 If the Gemini Door is required, see DESIGNER LINE DOOR STYLE OPTIONS  GEMINI and use the prefix "G" before the model number. If the Occult Door is required, refer to OCCULT SERIES and use the prefix "O" before the model number
 Select the door style from the illustrations.
 If the shelf is to be deleted with the valve installed at the top, insert the prefix "T" before "VC" and note the appropriate knockout location.
Model Number 
Trim Style and Projection 
Inside Box Dimensions H x W x D 
Outside Trim Dimensions H x W*** 
Rough Opening H x W x D 
Knockout Locations** E F G 
Interior Capacity 

VC4016R  Rec. 5/16  40 x 16 x 8  43½ x 19½  41 x 17 x 8¼  6" 4"  One 2½" Fire Dept valve with cap and chain and a Fire Extinguisher 

FS  VC4016R  Rec. 5/16  40 x 16 x 8  43½ x 19½  42^{1/8} x 18^{1/8} x 9^{1/8}    
VC4016RK  SemiRec. 1¼  40 x 16 x 8  43½ x 19½  41 x 17 x 7¼  6" 4"  
FS  VC4016RK  SemiRec. 1¼  40 x 16 x 8  43½ x 19½  42^{1/8} x 18^{1/8} x 8^{1/8}    
VC4016RL  SemiRec. 2½  40 x 16 x 8  43½ x 19½  41 x 17 x 6  6" 4"  
FS  VC4016RL  SemiRec. 2½  40 x 16 x 8  43½ x 19½  42^{1/8} x 18^{1/8} x 7    
VC4016RT  Trimless  40 x 16 x 8    x x8½†  6" 4"  
VC4016SM  Surface Mtd.  43½ x 19½ x 8½  43½ x 19½      
VC3616R  Rec. 5/16  36x 16 x 8  39½ x 19½  37 x 17 x 8¼  6" 4"  One 2½" Fire Dept valve with cap and chain and one of the following Fire Ext. MP2½,MP5, DC2½,DC5, MP6,MP10, DC6,DC10, CD5,HT5,HT11, HT15½,WC6L 

FS  VC3616R  Rec. 5/16  36x 16 x 8  39½ x 19½  38^{1/8} x 18^{1/8} x 9^{1/8}    
VC3616RK  SemiRec. 1¼  36x 16 x 8  39½ x 19½  37 x 17 x 7¼  6" 4"  
FS  VC3616RK  SemiRec. 1¼  36x 16 x 8  39½ x 19½;  38^{1/8} x 18^{1/8} x 8^{1/8}    
VC3616RL  SemiRec. 2½  36x 16 x 8  39½ x 19½  37 x 17 x 6  6" 4"  
FS  VC3616RL  SemiRec. 2½  36x 16 x 8  39½ x 19½  38^{1/8} x 18^{1/8} x 7    
VC3616RT  Trimless  36x 16 x 8    x x8½†  6" 4"  
VC3616SM  Surface Mtd.  39½ x 19½ x 8½  39½ x 19½     
NOTE: "FS" models denote Larsen's "FlameShield" firerated cabinets. When specifying Larsen's "FlameShield" firerated cabinet option for the VC3616 and VC4016 Series, refer to the dimension chart above and select the models with an "FS" prefix. No knockouts are provided with firerated valve cabinets. Pipe holes must be drilled by installer and complete instructions are supplied with each firerated valve cabinet. For complete details of the "FlameShield" option. 
** No knockouts are provided for surfacemounted cabinets unless specified. † Trimless cabinets must be installed before the drywall. Plaster stop must be behind the drywall. Trimless are not recommended for block wall installation. *** Deduct ¾ from HxW Dimensions for Cabinets with Aluminum Door & Trim. This does not apply to "FS" firerated option. 